|| IEC 60896-11 ed1.0 withdrawn corrigendum
|| Stationary lead-acid batteries - Part 11: Vented types - General
requirements and methods of tests
||This part of IEC 60896 is applicable to lead-acid cells and
batteries which are designed for service in fixed locations (i.e.
not habitually to be moved from place to place) and which are
permanently connected to the load and to the d.c. power supply.
Batteries operating in such applications are called "stationary
Any type or construction of lead-acid battery may be used for
stationary battery applications. This part 11 of the standard is
applicable to vented types only.
This first edition of IEC 60896-11 cancels and replaces IEC 60896-1
(first edition) published in 1987 and its amendments 1 (1988) and 2
(1990), and constitutes a technical revision.
This English-language version is derived from the original bilingual
publication by leaving out all French-language pages. Missing page
numbers correspond to the French-language pages.
||21 - Secondary cells and batteries
|Work in progress
|Project||Stage code||Forecast publication date|
|No project under development||-||-|