Tests for electric cables under fire conditions - Circuit integrity - Part 2: Test method for fire with shock at a temperature of at least 830 °C for cables of rated voltage up to and including 0,6/1,0 kV and with an overall diameter not exceeding 20 mm
Note: a redline version of this publication exists
IEC 60331-2:2018 RLV
This document is applicable to cables of rated voltage not exceeding 600 V/1 000 V, including those of rated voltage below 80 V, metallic data and telecom cables and optical fibre cables.
It is intended for use when testing cables of not greater than 20 mm overall diameter.
Cables of larger diameter are intended to be tested using the apparatus, procedure and requirements of IEC 60331-1.
This document includes details for the specific point of failure, continuity checking arrangement, test sample, test procedure and test report relevant to electric power and control cables with rated voltage up to and including 600 V/1000 V. Details for the specific point of failure, continuity checking arrangement, test sample, test procedure and test report relevant to metallic data and telecom cables and optical fibre cables are not given by IEC 60331-2.
Although the scope is restricted to cables with rated voltage up to and including 0,6/1,0 kV, the procedure can be used, with the agreement of the manufacturer and the purchaser, for cables with rated voltage up to and including 1,8/3 (3,3) kV, provided that suitable fuses are used.
Annex A provides the method of verification of the burner and control system used for the test.
Requirements are stated for an identification that may optionally be marked on the cable to signify compliance with this standard.
This second edition cancels and replaces the first edition published in 2009. It constitutes a technical revision.
The significant technical changes with respect to the previous edition are as follows:
– extension of the scope with metallic data and telecom cables and optical fibre cables, although details for the specific point of failure, continuity checking arrangement, test sample, test procedure and test report relevant to metallicdata and telecom cables and optical fibre cables are not given by IEC 60331-2;
– improved description of the test environment;
– mandatory use of mass flow meters/controllers as the means of controlling accurately the input flow rates of fuel and air to the burner;
– improved figure illustrating method of mounting of the sample regarding bending radius;
– improved description of the information to be included in the test report.
|Publication type||International Standard|
|Available language(s)||English, English/French|
|TC/SC||TC 20 - Electric cablesrss|
|ICS||29.060.20 - Cables|
29.020 - Electrical engineering in general
13.220.40 - Ignitability and burning behaviour of materials and products
|File size||1324 KB|
The following test report forms are related:
Share your publications
Learn how to share your publications with your colleagues, using networking options.
Our prices are in Swiss francs (CHF). We accept all major credit cards (American Express, Mastercard and Visa), PayPal and bank transfers as form of payment.
Keep in touch
Keep up to date with new publication releases and announcements with our free IEC Just Published email newsletter.
Contact customer services
Please send your enquiry by email or call us on +41 22 919 02 11 between 09:00 – 17:00 CET Monday to Friday.