Power transformers - Part 3: Insulation levels, dielectric tests and external clearances in air
Note: a more recent version of this publication exists
IEC 60076-3:2013+AMD1:2018 CSV
- Three categories of transformer are clearly identified together with the relevant test requirements, these are summarised in Table 1.
- Switching impulse levels are defined for values of Um > 72,5 kV.
- The procedure for Induced voltage tests with PD has been revised to ensure adequate phase to phase test voltages.
- The AC withstand test has been redefined (LTAC instead of ACSD).
- Induced voltage tests are now based on Ur rather than Um. - New requirements for impulse waveshape (k factor) have been introduced.
- Tables of test levels have been merged and aligned with IEC 60071-1:2010.
- Additional test levels have been introduced for Um > 800 kV.
- A new Annex E has been introduced, which sets out the principles used in assigning the tests, test levels and clearances in air.
Share your publications
Learn how to share your publications with your colleagues, using networking options.
Our prices are in Swiss francs (CHF). We accept all major credit cards (American Express, Mastercard and Visa), PayPal and bank transfers as form of payment.
Keep in touch
Keep up to date with new publication releases and announcements with our free IEC Just Published email newsletter.
Contact customer services
Please send your enquiry by email or call us on +41 22 919 02 11 between 09:00 – 17:00 CET Monday to Friday.