Surge arresters - Part 6: Surge arresters containing both series and parallel gapped structures - System voltage of 52 kV and less
a) A new concept of arrester classification and energy withstand testing was introduced: the line discharge classification was replaced by a classification based on repetitive charge transfer rating (Qrs) and thermal charge transfer rating (Qth). The new concept clearly differentiates between impulse and thermal energy handling capability, which is reflected in the requirements as well as in the related test procedures.
b) Power-frequency voltage versus time tests – with and without prior duty – were introduced as type tests.
c) Requirements and tests on disconnectors were added.
d) Definitions for new terms have been added.
e) Clause 10 contains particular requirements for polymer-housed surge arresters. These are indicated in the form of replacements, additions or amendments to the original clauses or subclauses concerned.
Keywords: testing of metal-oxide surge arresters
Share your publications
Learn how to share your publications with your colleagues, using networking options.
Our prices are in Swiss francs (CHF). We accept all major credit cards (American Express, Mastercard and Visa), PayPal and bank transfers as form of payment.
Keep in touch
Keep up to date with new publication releases and announcements with our free IEC Just Published email newsletter.
Contact customer services
Please send your enquiry by email or call us on +41 22 919 02 11 between 09:00 – 17:00 CET Monday to Friday.