IEC 60099-5:2018 RLV
Surge arresters - Part 5: Selection and application recommendations
IEC 60099-5:2018 provides information, guidance, and recommendations for the selection and application of surge arresters to be used in three-phase systems with nominal voltages above 1 kV. It applies to gapless metal-oxide surge arresters as defined in IEC 60099-4, to surge arresters containing both series and parallel gapped structure – rated 52 kV and less as defined in IEC 60099-6 and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines (EGLA) as defined in IEC 60099-8. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed. Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to when selecting the type and rating. Typical maximum residual voltages are given in Annex F. It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters. The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued. Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification. This third edition cancels and replaces the second edition published in 2013. This edition constitutes a technical revision. This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC 60099-4:2014:
a) Expanded discussion of comparison between the old and new classification and how to calculate or estimate the corresponding charge for different stresses.
b) New annexes dealing with:
- Comparison between line discharge classes and charge classification
- Estimation of arrester cumulative charges and energies during line switching
Keywords: selection and application of surge arrestors, nominal voltages above 1 kV
|Publication type||International Standard|
|TC/SC||TC 37 - Surge arrestersrss|
|ICS||29.120.50 - Fuses and other overcurrent protection devices|
29.240.10 - Substations. Surge arresters
|File size||8401 KB|
The following test report forms are related:
Share your publications
Learn how to share your publications with your colleagues, using networking options.