IEC 60079-31:2022 RLV
Explosive atmospheres - Part 31: Equipment dust ignition protection by enclosure "t"
IEC 60079-31:2022 is applicable to equipment protected by enclosure and surface temperature limitation for use in explosive dust atmospheres. It specifies requirements for design, construction and testing of Ex Equipment and Ex Components. This document supplements and modifies the general requirements of IEC 60079-0. Where a requirement of this document conflicts with a requirement of IEC 60079-0, the requirement of this document takes precedence. This document does not apply to dusts of explosives, which do not require atmospheric oxygen for combustion, or to pyrophoric substances. This document does not apply to Ex Equipment or Ex Components intended for use in underground parts of mines as well as those parts of surface installations of such mines endangered by firedamp and/or combustible dust. This document does not take account of any risk due to an emission of flammable or toxic gas from the dust. This third edition cancels and replaces the second edition published in 2013. This edition constitutes a technical revision. Main significant changes from the previous edition are:
1) Document has been restructured from edition 2
2) Fault current rating of interrupting contacts in clauses 4.3.1 and 4.4.1, major change type C1
3) Cells and batteries in clauses 220.127.116.11 and 18.104.22.168, major change type C2
4) Overload or malfunction condition for the determination of temperature class for "tb" converter fed rotating electric machines, major change type C3
5) Additional requirements for entry devices with dust ignition protection by enclosure "t", major change type C4
Information about the background of ‘Major Technical Changes’
C1 – Ex Equipment having Level of Protection "ta" shall be rated for connection to a circuit with a prospective short circuit current of not greater than 1.5 kA. For Ex Equipment having Level of Protection "tb" or "tc" which is intended for mains connection and intended to interrupt fault current above 10kA, the equipment shall have a rated maximum short circuit withstand current, be tested according to 22.214.171.124, and be marked according to Clause 7.
C2 – For Ex Equipment having Level of Protection "ta" which contains a cell or battery, only a sealed cell or battery shall be used. For Ex Equipment having Level of Protection "tb" and "tc" where there are sparking contacts or hot surfaces, and which contains a cell or battery, only a sealed cell or battery shall be used.
C3 – Table 2 now includes malfunction conditions for temperature class determination of Level of Protection "tb" converter-fed electric machines.
C4 – Annex A added for entry devices with Type of Protection "t" including cable transit devices.
The contents of the corrigendum of October 2023 have been included in this copy.
|Publication type||International Standard|
|TC/SC||TC 31 - Equipment for explosive atmospheresrss|
|ICS||29.260.20 - Electrical apparatus for explosive atmospheres|
|File size||1181 KB|
The following test report forms are related:
Share this page
Share your publications
Learn how to share your publications with your colleagues, using networking options.
Our prices are in Swiss francs (CHF). We accept all major credit cards (American Express, Mastercard and Visa, JCB and CUP), PayPal and bank transfers as form of payment.
Keep in touch
Keep up to date with new publication releases and announcements with our free IEC Just Published email newsletter.
Contact customer services
Please send your enquiry by email or call us on +41 22 919 02 11 between 09:00 – 16:00 CET Monday to Friday.